(B) MOUNTING PLATE
CONDENSATION DRAIN KIT
, the actual baffle
ATION OF A FRIGIDAIRE PTAC INTO A FRIGIDAIRE WALL SLEEVE unit to sleeve
Turn off electrical power before service or installation.
Refer to Table 1 for LCDI detection device images.
Table 1LCDI DETECTION DEVICE
(For Ducted Installations Only)
NOTE: Upward air direction should only be used on ducted installations.
/Energy Saver: Cooling
/Energy Saver: Heating allow the wall t control of the unit. When in wall ip Switches (Heating mode) accordingly in order to mode, the control panel will be disabled.
/Energy Saver ip Switches (Cooling mode)
This is the most efficient mode for electrical usage.
You can customize your unit additionally using the keypad configuration options.
To enter Keypad configuration
Connect the unit to power. Press and hold the "fan speed " and the "V " for 5 continuous seconds, within
30 seconds of the unit being powered up. If the unit has had power for more than 30 continuous seconds, keypad configuration cannot be made.
To scroll through the Keypad Configuration Options
Press and release the "fan speed" to select the keypad configurations.
The stored value will be displayed.
To modify configuration settings
Press and release the Setpoint " " or Setpoint " V " buttons.
To exit Keypad Configuration
Keypad Configuration will end on its own 30 seconds after the last button press or when the "mode" on the
Keypad is pressed.
There are 4 configuration options?
1. Fahrenheit/Celsius Display Switch: